Diesel generator cranks but won’t start
How to Start, Operate and Stop Diesel Generator Set Preparation before starting diesel generator set. The switch of the control panel should be turned off before Start the diesel generator set. Press the start button. If the start is unsuccessful, wait for about 20 seconds before Diesel. Dec 11, · HOW-TO Starting and bleeding a new diesel generator - YouTube. This short tutorial will explain the process of getting a new backup electricity generator up and running. it .
Of the 4 possibilities we have listed here, the most frequent fix9 out of 10 times, is to simply bleed the fuel pump. It can be also full of water or even the home to birds, blocking the air flow to smoother the generator not allowed it to start. Check for holes. Then use a flexi camera to check inside.
If you find water or home to birds etc. Metal fuel pipes can be bent or nipped to stop fuel flow- check all metal pipes for hidden damage. In either case a bund with fluids will NEVER allow the diesel generator to start instead it will crank then shut how to crochet for beginners step by step. Solution- clean the fluids out of the bunded area in the generator and also clean up the bund of the fuel tank.
Once cleaned then re-start the generator. Firstly lubricate all the moving parts of the louvres. Then check also that the electric motor that powers the louvres is operational. After all of the above your generator should be ready to Start. In reality, a generator will only have issues with starting if it has not been regularly serviced according to the manufactures specifications or the weather conditions have been ignored to the detriment of the generator.
Generator Smoking. Search — Knowledge Base. Talk to Us: Call Me. Technical Support. Quote Me. Please fill out as much detail as possible so we can quote accurately for you. Check the following:- Is the engine warm to the touch? If the answer is YESthen the block heater is working. Is the exhaust not blocked? If NO blockage, then this is fine Air filters not blocked with dirt or debris? Do you have fuel in the tank? Then the most likely issue is lack of fuel to the engine.
Is the fuel line cracked, constrained, bent or ruptured? Check Fuel pump is pumping fuel through the generator? Engine oil in the engine? Any coolant in the engine? Check the batteries — are the connections corroded, flat or even connected Is there water inside the lead acid batteries?
Most Obvious easy fix- Lack of fuel is the most likely cause because some air is in the fuel line. This causes the fuel to drop back and not enter the engine. Our video clip shows how to bleed the fuel in a modern diesel generator.
Check your generator manual for its location. Then gently turn the screw to allow the air to escape and then re-tighten once fuel begins to appear at the screw. Blocked fuel filters- lack of servicing and not renewing the fuel filters over time will cause them to become inefficient and finally block with dirt.
Replace the fuel filters. If all the above have been checked out, and operational, then the last resort will be a faulty solenoid. Replace the solenoid. Mostly likely fix Of the 4 possibilities we have listed here, the most frequent fix9 out of 10 times, is to simply bleed the fuel pump. Fuel — Generator has stood for many years and never been used? You have two options: Polish the red diesel fuel in the fuel tank Flush out the fuel, clean the fuel lines and replace with NEW clean diesel from a reputable supplier.
Fuel hoses can have perished and stuck together preventing fuel flow. Check that there are NO fluids around the generator floor or leaks within the bunded generator Also check the associated Bunded fuel tank that feeds how to redeem a amazon gift card on the kindle generator with fuel In either case a bund with fluids will NEVER allow the diesel generator to start instead it will crank then shut down.
Test the louvres can now open free and easily. Now re-start the generator. Call Me. Learn More. Generator Hoses need replacement. Why do I need a larger generator than my peak demand? Power Continuity Tips and Guides are subject to site inspection by qualified Engineers before implementation.
Power Continuity Terms and Conditions Apply. Power Continuity and Powercontinuity are registered trademarks. All content is copyright Power Continuity Ltd. Download our Free Power Calculator App.
How can we best help you? The information you want is just a click away. Get a Quote. Request Callback. Live Chat. Request a Callback One of our engineers is waiting to discuss your project with you. How do i lose weight in my stomach a Quote What do you require?
A Retro fit or building works? Mains board upgrade or Switchgear? Removal or Relocation? New Generator? New UPS? Parallel or redundant systems? Equipment Installation?
Tips for Starting and Running an Industrial Diesel Generator in the Cold
If you are in a remote location where you are unable to have grid power, consider also getting a small reliable gas generator to simulate the shore and let the block heater run for a few hours before attempting to start the generator up. Check Battery Charger: Make sure the battery charger is also plugged into the main/shore power and functioning. If the battery is dead, you will be going nowhere fast. How to Start a Diesel Generator Set for the First Time. A prime/base load diesel generating set will either have hand or electric starting. Note: On a hand start engine, please refer to the engine instruction book, which will advise on decompression for that specific engine. On electric start units. Sep 28, · Start the diesel generator set. a. Do not start the diesel generator set with load. b. Press the start button. If the start is unsuccessful, wait for about 20 seconds before trying again.
The switch of the control panel should be turned off before inspection, and be careful not to short-circuit the battery output electrode.
Re-clean and inspect the machine room to ensure that there are no flammable and explosive materials around the unit, ensuring smooth and unobstructed air in and out of the machine room. Thoroughly inspect and ensure that the electrical and control parts are connected correctly, in good contact, reliable, and without aging. Check the reliability of the fastener and throttle adjustment system, confirm that the operating mechanisms are flexible, lightweight, and reliable, and check the pre-tightening of the water pump belt, charger belt and fan belt.
Clean the surface of the generating set , especially the rotating part of the unit to ensure that there are no foreign objects, check to ensure that there is no coolant, fuel, oil leakage. Check to ensure that the oil level is between the highest and lowest marks and as close as possible to the upper limit.
Note that unfiltered fuel should not be injected into the diesel engine under any circumstances. Check the fuel quantity in the fuel tank and add suitable fuel if necessary. When the unit starts for the first time or stops for a long time and then starts again, check to make sure there is no air in the fuel. If there is air, loosen the air bleed screw on the diesel filter and pump the fuel to the air bleed screw with the manual fuel pump, drain the air in the fuel system, and tighten the bleeder screw.
Check the coolant level to be within 5cm of the filling cover to ensure that there is no obstruction outside the radiator. Do not operate the diesel engine without air filter. Check the air filter blockage indicator. If the indicator is red, replace the air filter. Close the power switch and check the battery voltage from the control panel. If it is less than 22V and cannot meet the startup requirements, the battery needs to be charged.
Do not start the gen set with load. Press the start button. If the start is unsuccessful, wait for about 20 seconds before trying again.
If the start is unsuccessful for 3 consecutive times, stop the start and remove the fault factors such as battery voltage or oil circuit before starting. Note that continuous start-up in a system that is not working properly will cause unburned gas to accumulate in the exhaust system, posing a potential explosion hazard. To start the diesel genset in a cold environment, preparation must be done.
Use winter fuel suitable for local temperature qualified brand. This can reduce the risk of waxy deposits in the fuel injection system. In the case of extremely low ambient temperature, it is recommended to install a preheating system water jacket preheating, oil heating, fuel heating and ensure that the cooling system is filled with antifreeze.
The battery must be in good condition. Low temperature will reduce the capacity of the battery. Depending on the actual situation, it may be necessary to increase the capacity of the battery. Manual, automatic, three-remote control cabinets and ATS cabinet in non-standard units, please refer to the corresponding random data for the use of the cabinet.
Check the oil pressure, water temperature, voltage, frequency, etc. If there is any abnormality, stop the machine immediately for inspection. After the fault is removed, the unit can be started again. Check the oil circuit, waterway, gas circuit and smoke exhaust system of the unit for leaks. Check the connection of the unit for looseness and severe vibration. Check whether the various protection and monitoring devices of the unit are normal. The gen set needs to be guarded when it is running.
Overloading is strictly prohibited. Do not short circuit when the unit is in operation, otherwise it will cause serious damage to the equipment. It is strictly forbidden to disassemble any parts of the generator set while it is running! Do not reach under the fan shield and any other parts that have relative motion! Do not try to touch the exhaust pipe, turbocharger, high temperature coolant, heater and other high temperature surfaces by hand, there is a danger of being burned!
Check the output voltage and frequency from the control panel. The output voltage of the unit has been adjusted at the factory, so it should be indicated within the normal range. For units with mechanical speed regulation, the frequency should be close to 52 Hz under no-load conditions; for units with electronic speed regulation or EFI speed regulation , the frequency is close to 50 Hz under no-load conditions. Keep the load on the diesel generator set not exceeding the rated value.
Before shutdown, the load must be unloaded, and it is strictly forbidden to stop with load. In general, after unloading the load, the diesel genset needs to run for 3 to 5 minutes without load before stopping. When the load cable is connected or removed, the battery's negative wiring must be turned off and removed. The unit must be shut down immediately if abnormal noise or odor is emitted during start-up or operation. When the unit oil pressure suddenly drops to the limit or no oil pressure, the fault light is red and must stop immediately.
The machine must stop immediately:. When the unit water temperature suddenly rises above the specified value and the fault light is red. When the unit output voltage exceeds the maximum reading on the meter. When there is a fire, electric leakage or other natural disaster that may endanger the safety of the crew and operators. At this point, press the emergency stop button or push the stop control handle of the fuel pump to the stop position rapidly , the unit will quickly cut off the load, and immediately turn off the throttle, while the red "emergency stop" indicator light is on.
The button needs to be re-screwed to release the emergency stop signal. When the power generating set is in normal operation or is supplying power to the equipment, if there is no special emergency, it is recommended that the user do not perform emergency shutdown operation at will. Check for leaks in the engine and machine room.
Close the fuel valve. If the unit is to stop for a period of time, turn off the main switch. Long-term shutdown should drain fuel and cooling water, and periodically charge the battery according to maintenance specifications. All Rights Reserved Sitemap. Home Products News Contact Us. Start the diesel generator set a.
Do not start the gen set with load b. Diesel generating set is in operation a. The machine must stop immediately: a. After shutdown a. Close the fuel valve c. Recent Articles Technical Specificat Maintenance Method o Under What Condition Inspection Methods o How to Solve Reducti Generator Sets Diesel Generators Generators Diesel Engine May Jun Jul Aug Sep Oct Nov Dec Jan Feb Mar Apr Generator Sets.
Diesel Generators. Diesel Engine. Contact Us Adds: No. Follow Us.
<- What does grabar mean in spanish - What to expect when you take the morning after pill->